Heat Pump Modular type V-III TROPICAL Series AJY270LNLBHH [3Phase]
- Excellent energy saving
- High design flexibility for various building air conditioning
- Easy installation and maintenance
- Energy saving technology that boosted operation efficiency
- Heavy anti-corrosion treatment design
- Powerful cooling capacity design
|Rating Capacity Range||30|
|Maximum Connectable Indoor Unit*1||50|
|Indoor unit connectable capacity||42.4 - 110.2 kW|
|Input Power||Cooling||21.36 kW|
|Air Flow Rate||13000+11100×2 m/³h|
|Sound Pressure Level*2||Cooling||63 dB(A)|
|Sound Power Level||Cooling||84 dB(A)|
|Maximum external static pressure||82 Pa|
|Compresor motor output||11.0+7.5×2 kW|
|Heat exchanger fin||Blue fin|
|Net Dimensions||Height||1690×3 mm|
|Net Weight||279+255×2 kg|
|Global Warming Potential||2,088|
|Connection Pipe Diameter||Liquid||19.05 mm|
|Operation Range||Cooling||-5 to 46 °CDB|
|Heating||-20 to 21 °CDB|
- Specifications are based on the following conditions.
- Indoor temperature of 27°CDB / 19°CWB, and outdoor temperature of 35°CDB / 24°CWB.
- Indoor temperature of 20°CDB / (15°CWB), and outdoor temperature of 7°CDB / 6°CWB.
- Pipe length:
- 7.5 m; Height difference between outdoor unit and indoor unit : 0 m.
- Minimum connectable indoor unit number is 2.
- The noise value is the value when measured in an anechoic room. When measured in the actual installed state,
- surrounding noise and reflections are received and the measured value is usually larger than the indicated value.
Outdoor Unit : AJY126LNLBH / AJY072LNLBH / AJY072LNLBH